## Heat Loss from Insulated Pipe

Heat loss/gain takes place from a pipe carrying hotter/ colder fluid than ambient temperature. Insulation reduces the heat loss to surroundings. Heat loss depends upon number of factors like insulation thickness, ambient temperature, wind speed etc. This article shows how to calculate heat loss from an insulated pipe and a bare pipe to surroundings.

Example

A 3" Carbon steel pipe is carrying hot oil at 180°C and insulated with 50 mm thick calcium silicate insulation. Insulation is cladded with a sheet with surface emissivity of 0.9. Ambient temperature is 28°C and wind velocity is 3.5 m/s. Calculate surface temperature and heat loss from insulated and bare pipe.

Overall heat transfer coefficient of an insulated pipe is defined as following.

where, k_{PIPE}, k_{INSULATION} are thermal
conductivity of pipe and insulation. h_{in} is heat
transfer coefficient for fluid flowing in pipe and h_{air}
is heat transfer coefficient due to air flowing outside the
pipe. The first two terms of denominator in above equation are
generally smaller compared to remaining terms and can be
neglected. For this example first term due to pipe fluid is
ignored.

**Air Side Heat Transfer Coefficient, h _{AIR}**

Air side heat transfer is due to combined effect of convection
and radiation. Assume a temperature at cladding surface
*t_surface* and steel pipe surface *t_interface*.
Calculate average air film temperature as following.

` t_average = ( t_surface + t_ambient )/ 2`

Estimate thermodynamic properties of air like thermal conductivity (k), viscosity (μ), expansion coefficient (β = 1/t_average), air density (ρ), kinematic viscosity (ν), specific heat (Cp) and thermal diffusivity (α) at average air film temperature. These properties are available in literature in form of tables, these can be fitted into a polynomial form using excel's LINEST function. Reynolds's number (Re), Prandtl number (Pr) and Rayleigh number (Ra) are calculated based on above properties.

**h_radiation**

Heat transfer coefficient due to radiation is calculated using following relation.

` h_radiation = σ ε (t_surface`^{4} - t_ambient^{4})/ (t_surface - t_ambient)

where σ is Stefan Boltzmann coefficient and ε is emissivity for cladded surface.

**h_convection**

Convective heat transfer coefficient comprises of forced and free convection. Forced convection can be modeled based on correlation by Churchill and Bernstein.

` h_forced = Nu.k_air / D3`

Free convection is calculated based on correlation by Churchill and Chu.

` h_free = Nu.k_air / D3`

Combined heat transfer coefficient due to forced and free convection is calculated using following relation.

`Nu_combined = ( Nu_forced`

^{4}+ Nu_free^{4})^{0.25}`h_convection = Nu_combined.k_air / D3`

Air side heat transfer coefficient is calculated as following.

` h_air = h_radiation + h_convection`

**Overall Heat Transfer Coefficient, U**

Thermal conductivity for insulation material and pipe is available in literature and depends upon temperature. It can be fitted into a polynomial equation using LINEST function in excel. Heat transfer resistance due to pipe and insulation is calculated using following relation.

`r_pipe = D3.ln(D2/D1) / 2.k_pipe`

`r_insulation = D3.ln(D3/D2) / 2.k_insulation`

Overall heat transfer coefficient is calculated as.

`r_overall = r_pipe + r_insulation + 1/h_air`

`U = 1/r_overall`

Heat flowing through insulation is estimated.

` Q = (t_operating - t_ambient)/r_overall`

A revised estimate for interface and surface temperature is made.

`t_interface = t_operating - Q.r_pipe`

`t_surface = t_interface - Q.r_insulation`

Above steps are repeated with these new estimates till there is negligible difference in temperature.

Heat loss per unit length of pipe is estimated as following.

` Heat`_{Loss} = πD3 Q

**Bare Pipe**

For heat loss from bare pipe all above steps are repeated with resistance due to insulation not considered.

`r_pipe = D2.ln(D2/D1) / 2.k_pipe`

`r_overall = r_pipe + 1/h_air`

For this example surface temperature and heat loss are as following.

Resources

- Spreadsheet for Heat Loss from Insulated Pipe